Better Touch Better Business
1. Before installing the high-efficiency filter, the clean room must be fully cleaned and wiped. If there is dust in the air-conditioning system, it should be cleaned and wiped again to meet the cleanliness requirements. If a high-efficiency filter is installed in the technical interlayer or suspended ceiling, the technical interlayer or suspended ceiling should also be thoroughly cleaned and wiped.
2. The clean room must be sealed during installation, the FFU is installed and started to run, and the air conditioner must be tested for trial operation, and it must run continuously for more than 12 hours. After cleaning and wiping the clean room again, install the high-efficiency filter immediately.
3. Keep the clean room clean and free of dust. All keels have been installed and levelled.
4. Installers must be equipped with clean clothes and gloves to prevent artificial pollution of the box and filter.
5. In order to ensure the long-term effective work of the high-efficiency filter, the installation environment should not be in oily smoke, dusty and humid air. The filter should try to avoid contact with water or other corrosive liquids, so as not to affect its use effect.
6. It is recommended that the number of installers in each group is 6.
Suzhou Pharma Machinery Co.,Ltd.
Copyright © 2020 SUZHOU
CO.,LTD. | All Rights Reserved